- Pump Steam Trap
- Pump Steam Trap
Pump traps use the trap principle, relying on steam, air and other gases as power to transport condensate from the low pressure area to the high pressure area, or from the negative pressure area (vacuum) to the normal pressure area.
The condensate recovery pump has a series of advantages such as automatic control, no cavitation, simple maintenance, no electricity, water hammer resistance, large displacement, explosion-proof, no noise, and the pressure of the power steam determines the head. It is unmatched by other electric pumps.
It is widely used in the recovery of steam condensate and the transportation of low-viscosity non-volatile liquids.
The pump trap has two strokes:
1.Inlet water and exhaust steam: At the beginning, the inlet check valve is opened, and the outlet check valve is closed due to high back pressure. At the beginning, the water inlet and exhaust valves in the valve are opened, and the float is in a low position. As the water level rises, the float When reaching the highest, the controller is in the state of switching zero boundary.
2.Inlet steam and drainage: the controller starts to switch at a high position and closes the exhaust valve; opens the power steam, injects steam into the valve, and pushes the condensate in the pump to the high pressure area under the push of steam pressure, then the inlet check valve Due to the high pressure inside the valve, water cannot enter. When the float reaches a low position, the controller switches to close the power steam, opens the exhaust valve, and enters the next action cycle.
● It is recommended that the head height of the fluid entering is0.5m or more (the pump cover is the reference), you can refer toTake the "Correction Factor for Water Ingress Height";
● The power steam inlet is connected to RC1/2”;
● For the normal operation of the pump, the saturatedcondensate needs to be flashed or condensed.The type system must ensure the pressure difference and backpressure rate for the normal operation of the trap.
● The standard configuration of condensate inlet and outlet isHG/T20592-2009 PN16 flangeFor connection, if you need other standards such asASME16.5, JIS, etc., please specify.
Step 3: Shift the intersection point to the left to find the displacement value, and get the displacement of 3.5t/h.
Step 4: 3.5t/h x head height correction factor = actual displacement;
1.Its not driven by electric power, driven by steam or compressed air, is explosion-proof and safe, and can be used in any environment.
2.The structure is compact, and there is no requirement for installation, Even in the wild, it will not affect its normal operation.
3.Automatic control, the amount of water output is determined by the amount of water input. When the amount of condensed water increases, the working frequency speeds up, when it decreases, the working frequency decreases, and no condensed water enters and stops working.
4.No cavitation work, completely overcome the shortcomings of electric pump cavitation
5.All stainless steel internal parts and special materials guarantee performance and life